I moved into a new home and several receptacles have the hot and neutral reversed. I confirmed this with a basic receptacle tester. I opened one up and found the white wire on the brass terminal, and the black wire on the silver terminal.
Is there any scenario where this would have been done on purpose? Perhaps as a workaround for some other issue? If not, then I would assume I could safely correct it myself.