I'm struggling finding a power source for the cabinet lighting in our remodel. The breaker box is very full and I'd rather not re-wire/double up breakers are this time.
Is it ok to pigtail off of one of the LINE inputs of a 20A kitchen GFCI?
These are all LED lighting, which I've read about the issues with GFCI cicruits and LEDs on the load side. Hence, pigtail off of the LINE side.
It would be fed into a metal 4x4 box and conduit.