I am adding a new lighting circuit to my bathroom remodel and wanted to get some feedback on my planned wiring layout. This circuit is in addition to a pre-existing dedicated 20A circuit for the outlets.
I am going to feed a 3 gang box with a 14/2 15A circuit from my breaker box. Then pigtail the hot and neutral to 1 dual dimmer switch, and a deadface GFCI.
From the dual dimmer, I was going to run 14/3 to a vanity fixture and 2 pot lights, sharing the neutral.
The second run will go to the GFCI, then to a dimmer and timer combo, then a 14/3 run to a pot light in the shower and an exhaust fan, also in the shower wet area. This run will also share the neutral.
My original plan was to run 14/2 from each switch to each fixture, but it would seem more efficient to pull 2 14/3 runs rather than 4 14/2 runs, especially due to challenges in the structure to get the wiring thru.
Thoughts on this layout being code compliant? Any opinions for improvement?