Ok, I just failed my inspection. The inspector made some good catches. The only thing I question is he said all outlets in the detached workshop need to be tamper resistant. We are still on the 2014 NEC, and I thought I only needed tamper resistant outlets in the house. Does the shop really need TR outlets?
Yes it is required by the 2014 NEC, the 2014 Code says:
406.12 Tamper-Resistant Receptacles. Tamper-resistant receptacles shall be installed as specified in 406.12(A) through (C).
(A) Dwelling Units. In all areas specified in 210.52, all nonlocking-type 125-volt, 15- and 20-ampere receptacles shall be listed tamper-resistant receptacles.