I will be installing a ceiling fan/light kit in our bedroom that did not have any sort of ceiling fixture before. Currently, the only light switch in the room is a two-way switch that controls the top half of a wall outlet (the jumper tab is broken off on the outlet).
My plan was to install a double-gang box in the wall where the current light switch is and run the new 14/2 cable through the attic to the new fan. When I took out the existing light switch i noticed this configuration, where the white wire is always hot and the black is switched hot:
Then within the box is the following:
I know it may be tough to make out but one set of nutted wire are two white wires coming out of the wall. The second set are three wires, the black and white coming from the switch and a red line wire coming from the wall.
My question is, if I want to add a second light switch for independent control of a new ceiling fan, how do I tie that into the current wiring configuration?