I have an existing dimmer and a toggle switch configured in 3-way configuration.
The toggle switch has a single 12/4 attached.
The dimmer has 2 12/3s (I guess). Both of the grounds are wired to a common ground. One of the 12/3s has the black wired to the dimmer and the white wired to common neutral. The second has a white and a red wire wired to the two red wires coming out of the dimmer.
I'm a little befuddled by the configuration. It seems like maybe the red/white pair are the travelers for the remote toggle switch, but I'm confused by the black wire coming out of the remote switch's 12/4.
It seems like maybe that's going to load (it's a light fixture). But, if that's going to load, what's going on with the other 12/3 in the dimmer box?
If any of that makes sense to you, is there a ZWave dimmer I can put here?
I may be describing the wires incorrectly. In my count, I'm including ground.