I trying to move a switch, which is currently in a 2-gang box. The 2-gang box will need to stay in place (and covered with a plate) as it is also the junction of some other stuff (currently power comes into the box, and feeds the switched light, and 2 branches of outlets). With new codes, I need to have a grounded neutral in the relocated switch. My plan is to do the following:
Note, I have excluded all the other stuff that is in the existing 2-gang box. My question is- what do I do with the neutral in the 1-gang switch box? My existing toggle switches do not have a connection for a neutral (they are not "smart" switches). Do I just cap the neutral line in the single-gang box? Are there new toggle switches that accept a neutral?