Is this properly connected or need to be changed? Note: Bare ground wire connected to both A and B metal boxes and to green screws on outlets A and B
Wired used from main Panel to both A and B outlet is 12awg/3 with ground, Red, Black, white and bare ground.
From main panel to 1st Outlet A, cut the red wire in the box and connected the end side of the wire from main panel side to Brass screw on line side of outlet, the other end of the red wire capped and taped inside box, the remaining red wire between box A and box B is now (Dead wire.) White wire cut in box A and connected one end on the silver screw line side of outlet and the other end connected in the hole behind outlet on same line side, (Instead of Pig Tail wire) Is this good not to use pig tail this wire section continues to outlet B and connected on silver screw on line side and now the Black wire connected on brass screw line side and the red end wire also capped and taped in Box B. In Main Panel I used a Double 20A pole breaker. On the outlets the LOAD side screws did not use them at all. Thank you.