San Bernardino Ca. area. 20 amp circuit #12 wire, Can I use this circuit for Lighting? On this circuit 5 20 amp outlets and 6 LED fixtures 50 watts each. One outlet will be used for a refrigerator.
If this is one of your 2 20A small appliance circuits the lighting should not be on it NEC handbook exhibit 210.28. I think it is always a bad idea to have a refrigerator on a small appliance circuit but it is allowed by code. If this is in addition to the 2 small appliance branch circuits for the kitchen countertop area it is legal.