I'm wiring the new workshop and want to use 3 way switches to control four outlets running across the ceiling for plug in lights. Right now, each switch is functioning like a single pole, turning on/off the string of outlets rather than controlling the outlets as intended. Power comes into the first 3-way; Red traveler is continuous from first to second switch; black traveler runs from first switch, ties into each outlet, and ends at second switch common; white neutral comes from power and ties into each outlet; white wire is used as hot wire from last outlet to second switch.
Where did I make the mistake? Thanks for the help.