Re-wiring the garage and running into an issue with a switched outlet. The outlet is in the middle of the run (after a GFCI and before a single ceiling outlet for the door opener). I've split the receptacle to only have the top outlet switched and all of the hot outlets are working as expected. Unfortunately the switched outlet trips the breaker each time it's switched on. The wires coming into this box are: 2 wire from GFCI (from load) 2 wire from switch (white taped as 'hot') 2 wire from next outlet
Connections as follows: - Ground from outlet to raised ground screw - Black from GFCI, Black to next outlet, Switch loop (white from switch), and pigtail are nutted and connected to bottom brass screw - Black from Switch connected to top brass screw - White from GFCI, White to next outlet, and pigtail are nutted and connected to bottom silver screw
Any suggestions are welcome.