I've been trying to install a four way switch setup for a ceiling fan using a Leviton z-wave control switch and two matching remotes.
I've attached a copy of the wiring as it is currently set up. I'm replacing old switch so have had to do a bit of guesswork as to what line is what.
The thing that has been throwing me off is this extra switch, that I initially thought had nothing to do with the light at all. When I pulled everything out of the gang box though it was spliced in with the switch neutral wire.
It seems like this is an extra switch before the load, and then the other three are after the load. I don't know why it's there though, since two of the switches are in the same gang box.