We recently put an addition on our home. I am looking to run a subpanel from our 200 amp service panel out in the yard at the meter (mounted to a pole), 75' to subpanel location.
In the addition we have 2 bedrooms, walk in closet, laundry room and bathroom. We also added on to our living room 10x15. All these rooms will have receptacles, lights and a 240 volt hook up for the dryer in the laundry room and baseboard electric heaters. (1 per room except laundry and living room) Total of 4 heaters. I currently picked up a 125 amp homeline 20 space 40 circuit panel box without main breaker. Is a 100 amp breaker from main panel more than enough? Can I use a 60 amp breaker to feed the subpanel? This is going to be inspected per NEC code.