I have a Coleman gas furnace in a wall space in my house which somehow shares the blower on my a/c unit on the roof because it turns on when furnace is called to start, though it does bump up after a few minutes when the furnace ignites (which tells me it has its own blower motor) and both are controlled by a single thermostat and shuts off when satisfied.
My problem, only 1/3 of my house is getting warm air blowing through the registers other 2/3 is mild to cold air. All registers have adequate air flow. It causes our room to get very warm while others are cold. In the summer I had a Freon leak and they took the a/c unit somewhat apart to find it. Not sure if somehow they put it back together incorrectly and there lies my problem. I have yet to go in the attic or on the roof. Any suggestions or leads would be helpful.