Will this still provide GFCI protection? Is this against code? Does this represent a hazard?
I have a subpanel with a 60A GFCI circuit breaker, that I want to use that to feed to 2 30a 240v receptacles. I'm looking to have GFCI protection on the lines, but also make sure the lines are protected for their rating.