I have a junction box with 2 switches:
- Right switch controls the ceiling fan.
- Left switch does nothing, but the black(hot) wire is labeled "Fan". The white neutral wire is not attached.
I'm trying to wire one of the outlets to be a half-switch controlled by the extra switch.
- all the outlets have 2 black wires attached to them and 2 white wires.
Is this possible without running additional wiring?
I had the house fully renovated last year but the GC did not ask me how I wanted to rooms wired despite me clearly stating this was to be the case.