I have recently changed a light fitting which I have done a hundred times before but this time the switch won’t turn off.
The cables from the ceiling are twin and earth, the light fitting is double insulated so no need for the Earth cable so we just take this off.
We have a loop the two red wires in a connector and placed the other red live wire into the live connection to black wires into the neutral connection and the switch wire, which is a black wire with a red sleeve into the other live position, there is power going to the light, but the switch does not turn it off so it is on permanently
We did remove the rose before taking a photo, but have this photo of another light in the house.
Ruskes are you saying to remove the red wire from the N position?
The earth cables have just been taped up, we haven’t done anything else with them.
Can you tell me what what you think I need to do with the wires to correct