I’m looking for advice on how to bring this conduit run up to code, 2 issues in particular:
- Securing the conduit to the end of the stud, which I believe is required within 3’ of the box. Are nail straps still allowed for this purpose? I found one on Lowes.com but it did not say UL listed.
- Securing the cable coming out of the conduit at the top (x mark)*. Since the cable is perpendicular to the joist supporting the conduit, I can’t attach the cable there. It is however supported when it passes through the joist to the left. Does this count as adequate support, or do I need to use some kind of conduit or pipe hanger?
*I also planning on replacing that cable with flexible conduit, but I believe FMC has the same support requirements.