I have an induction cooktop/stove in a California condo built in 2011-2012.
Recently, I had to pull the cooktop electrical and discovered that the stove has a 3 wire harness (red, black, yellow/green). The building has 4 wires (red, black, white/neutral, and ground).
The builder connected the stove's yellow/green to the building's neutral and left the building's ground unconnected.
Per the manual, I believe they should have connected the stove's yellow/green wire to ground. However, the manual indicates it would be a bare wire and it's actually a yellow/green.
What's the correct way to wire the stove up to code?