I have a unused 20amp double pole circuit breaker (240/250V) at the panel. I would like to use it to control one 240V outlet (with L1, L2, G connections, no neutral) and two 120V outlets.
My thinking is that I need to pull four wires from the panel, all 12awg, and wire the first (240V outlet) with L1, L2, G; then continue from there to the two separate circuit 120V outlets, the first with L1, N, G, the second L2, N, G.
Is there anything safety-wise or code-wise that would disallow such a setup?
The devices plugged into these outlets would be small kitchen appliances for 120V and an electric kettle or electric grill running on European voltage (I will change the plug at the device cable) for the 240V outlet.