So mother in law wants white outlets/switches/plates. (she has old almond colored ones) So I get to two outlets in her bedroom....one red, one white and one black in. Take out the old outlet, put new outlet in with same wire set up. Get to the switch....one red on top and one black on the bottom. I can see in the box that a neutral is butterflyed with the black and red. Put in new switch with the same wire set up. Turn on the breaker and the outlets work, there is power. They don't shut off with the switch however. Basically the switch does nothing.
I'm guessing the wiring in the switch is wrong somehow, but don't know how since I did everything exactly how it was set up originally. Any guesses?