I have two separate lights in my room with two switches in the same box and am upgrading to two smart switches. The switches I bought have a neutral and I don't seem to see them in the box. Can anyone tell me if there is a neutral in here? This is a newer home if that matters and also there is a red wire that is capped off (orange cap in picture) and not connected to anything. Thank you!
You are in luck. The big group of white wires on the left of your picture are your neutrals. They need to remain hooked up together. You can see the bare ground wires twisted together in the back of the box. You'll be able to trace your always hot wires back to the group on the right. If you ever run into the painter that did the house, thank them for painting the inside of the junction box. :-)
Be careful what you are doing, you are not very experienced with electricity, and it can kill you.
On top, someone spray painted the wires in the box and now they all look white.
Here are your neutrals
Also that neutral nut, is probably at its capacity (it already has 4 wires). So adding two more might be a problem. Get a bigger nut, or splice one of the neutrals.