I recently ran a wire on a known 15 amp breaker to an outdoor GFCI outlet. Have 120 volt at the tie in, 120 volt at the outlet, all good. Then last night I lost all power at the outlet, now shows basically zero volts. Double checked all connections, no change. Breaker is good, wiring is intact, things before the tie in are still working... I'm lost. Ran 14/2 for 25 feet. From there it does a pig tail one line to a ring camera the other to said GFCI outlet, no voltage on those lines. Any ideas?