# What is the name of this electric circuit?

Hotline to L1 on both switch Common (or) traveler connecting the COM on both switches Load goes from L2 on both switches (To light)

My house is wired this way. Is there a US electrical reference that I could give a switch supplier? (Zooz)

EDIT: Adding the colors of wires in my boxes, I have neutral in the box but they are just a pass through.

• In the US, that type of switch is called a 3-way (in the UK/Commonwealth countries it's called a 2-Way) and that setup is wired abnormally for a US 3-way. Mar 17, 2022 at 14:40
• Mar 17, 2022 at 15:13
• I keep staring at the diagram, and it really looks to me like this won't function as I would expect for a three way switch. It looks the light is on when the switch on the left is in the down position (no matter what position the switch on the left is), and when the switch on the left is in the up position, the light is turned on or off by the switch on the right. Am I crazy? Mar 17, 2022 at 17:10
• @MatthewBourque -- it does work Mar 18, 2022 at 2:22
• @MatthewBourque: I think what's confusing is the way the switches are drawn. I originally assumed that they would switch the right-hand contact between the two left-hand contacts and got the same conclusion as you did. But I think they're actually supposed to switch the top left contact (marked with a white circle) between the two bottom contacts (marked with yellow dots). Interpreted that way, the circuit matches the "California 3-way" pattern. Mar 18, 2022 at 13:40

In the U.S. it is called a "California 3-way" or a "coast 3-way".

It was commonly used in the knob-and-tube days, when current-balancing was not yet a requirement. It is no longer installed by U.S. electricians.

It is quite safe if all the conductors are bundled into a single cable or conduit. Sometimes this requires a 12/4 or 14/4 NMS cable, which can be hard to find.

The circuit in your drawing can easily be converted to a modern traveler-pair 3-way. If you do this you will no longer be in conflict with the assumptions of the Zooz people. Ecnerwal describes how to do this in his answer, and FreeMan has modified your drawing to show the changes.

• A California 3-way like the OP's is still legal to install to Code (using 12/4 for the run between the switches if neutral, switched, hot, and traveler all need to run together, but they don't in the OP's case). The main reason they're not installed is because you can't use them for any more than 2 locations, best I can tell Mar 18, 2022 at 2:21
• @ThreePhaseEel: Agree (cf. my par. 3). I think the main reason no one uses this any more is that it only saved copper over the traveler-pair method when current did not need to be balanced, and a separate neutral path could be wired. Mar 18, 2022 at 2:50

Stock US 3 Way - change your wiring connections.

Line Power into first switch on the black terminal.

Both Travelers between switches on brass terminals.

No connection directly from first switch to Load.

No connection directly from Line power to second switch.

Drawn with white neutral, not pink. You end up with an extra wire between boxes. It doesn't matter if you use the "orange" or the "black" for the second traveler.

• I've added an edit of the OP's drawing that I'm 99% sure is correct. It is based on the presumption that the single screw on the right of each switch is the BLACK screw, and the pairs on left of each screw are the BRASS screws. (Mostly because it was easier to draw it that way.) If I have this wrong, do not hesitate to remove the drawing - I won't be offended! Mar 17, 2022 at 16:24
• @FreeMan: You should post the modified diagram as an answer. Querent's question no longer makes sense with the modified picture. Mar 17, 2022 at 16:58
• @A.I.Breveleri the drawing does not in any way change the original question, it illustrates the answer. Mar 17, 2022 at 17:01
• This is the code compliant way to install a pair of 3 way switches in existing homes. Modern code requires the neutral at at least 1 switch location but some states have not accepted this requirement Minnesota has adopted the 2020 version so it is likely all new construction will require the neutral. For existing prior to the 17 code no neutral was required at the switch box. Mar 17, 2022 at 17:07
• @ecnerwal, the house was built in 1967 and this is a finished basement. The switches have been wired this way for 55 years. It doesn't seem reasonable to change my wiring. I have multiple 3-way switches in the house that are wired the same way. Mar 19, 2022 at 12:33

## Doesn't matter, you'll rewire anyway

Smart switches don't depend on the usual "common + 2 travelers" arrangement. You are going to be re-wiring both boxes to match the requirements of the smart switch.

The only thing you need to identify is the cable between switches (a cable is several wires bundled together in a sheath). Then, assign the colors in that cable according to the instructions. Which will require that you re-define every wire, since these smart switches use the wires completely differently. As such, the prior configuration does not matter.

A common mistake here is to "not read the instructions" and expect it to wire like a common 3-way switch.

Their instructions show the wiring "before", but you only need to concern yourself with cable identification. You'll be re-defining what all the wires do.

Weirdly, their "before" drawings show only 1 traveler. I guess they never got the bulletin on how "conventional" 3-ways work, as they have 2 travelers. Well, it doesn't matter.

• Do modern smart switches require a neutral? Do they require a line hot which stays at the same contact on the switch and is not momentarily interrupted when another switch is flipped? Mar 19, 2022 at 16:28
• @JimStewart Have to get power somehow. Leaking it through the bulb is bad because modern LEDs will glow if you do. UL approves some current being bootlegged off ground, but only 0.5 milliamps, which is not enough to transmit WiFi or illuminate. Mar 19, 2022 at 19:26

The actual name of this circuit is California, West Coast three way circuit. By strict definition, this type of circuit didn't have any neutrals in the switch boxes so it's a "modified" California three way. Follow @Ecnerwal's instructions if you are going to change to normal conventional wiring.

• @Nayuki traveler from each switch has connection to hot and the other traveler from each switch has connection to load. The commons on each switch are connected together. It does match and depends on the configuration of the three way switches.
– JACK
Mar 18, 2022 at 15:43
• From the OP's added drawing it appears that there is a /4 cable between the two switches. Mar 19, 2022 at 16:38
• @JimStewart It looks like that too but the neutrals are just loose in the box.Thanks, I'll take the neutral "reference" out of my answer.
– JACK
Mar 19, 2022 at 19:11
• The OP said the neutral was "just a pass through". I take this to mean that the neutrals of the cables are connected to each other and are not just loose. In his added drawing he left off showing the neutral in the cable with the incoming line hot, so it's ambiguous. The second drawing shows an entirely different routing for the line hot and neutral from the first diagram. In the first drawing this cable goes into the load box; in the second drawing the line hot cable goes into a switch box. Mar 19, 2022 at 20:15
• @JimStewart I didn't mean loose loose..... just loose lol. Yes, it's an intact neutral but just there encase someone needs one in the future. Yes, routing of the hot and neutral is different from the first drawing. I just assumed it was an oversight or just an electrical representation rather than a physical one. We have all beat this one to death... hope I don't have to look at it again ... lol
– JACK
Mar 19, 2022 at 21:20