Are all components required to be weather resistant under an outdoor overhang? My understanding is that it’s considered a “damp location,” but it’s not clear to me what components are allowed. Is FlexMC allowed? Is this metal box allowed?
First that is a damp location but that looks like EMT or another type of conduit possibly nm but yes conduit is allowed in that location.
The shallow KO box is also allowed in that location things would be different if in a wet location but under that overhang it is code compliant
I would be more concerned with the festoon lighting string being in the drip zone of the roof is that string UL listed?