The previous owner put in a sub panel. 6awg plus ground is feeding it with a 50 amp breaker at the main. It is in an attached garage. I’m going to fix what he did with the bonding.
What is the metal at the arrows one going to the bar on left and one not completely going to bar on right? Just wondering if I have to do anything with this.
To fix this I’m going to leave the neutrals on the bar on right. Is it OK to put 2 bars for grounding where I circled? 2 separate bars due to the wire length coming in. And do the 2 grounding bars have to be connected?
One more question. Want to put a single pole 30 amp breaker for an RV outlet and a double pole 30 amp breaker for a dryer. Can the AC in the camper run the same time as the dryer?