My living room has 2 switches. 1 controlling the ceiling fan the other switch controlling the ceiling fan light. From the panel, I believe it's 14/2 into the box, pigtailed to the two switches, then it goes 14/3 to the ceiling fan box.
I want to add 4 recessed lights, can I just run 14/2 wire from the recessed lights to the ceiling fan box and connect white to all whites, ground to all grounds, and black to black, leaving the red (from switch) to black (to the ceiling fan / light combo)?
Resulting in me controlling the ceiling fan and light on 1 switch and recessed lighting on another or am I missing something here?
Is this also a multibranch? Would this be considered shared neutrals? (I don't believe so since the neutrals are all tied in the switch box.)