I'm planning to run a four 10g wire 30 amp circuit to supply 240v for an electric dryer. I'm wondering if I can add a 120v outlet to this and only use one outlet at a time on the same circuit, instead of adding a separate dedicated 12g wire 120v circuit on a separate 20amp breaker. Is the possible?
Looking for the flexibility to switch between a 240v dryer and a 120v dryer without rewiring when the user switches their appliance. This is to be the solution to a laundry room's required 120v outlet.
This is for a residential service.