House has a 50A, 3-line service to the old Range.
Want to instead have a separate Cooktop and an insert Oven located below it for a sleeker more integrated look. Each have a 30A requirement.
Can they both connect to the 50A feeder?
We have no good way to replace it with 2 separate circuits without replacing the whole electrical panel, and massive damage to ceilings, etc. to get it there.
Is it possible to share?
A range would have just as many burners and an oven on that same circuit, so it seems plausible. Could replace the 30A cords on the appliance with 50A? Or is it possible to fuse the 30A appliance cords in the J-Box before connecting to 50A home run? (We'd need the J-box concealed in the cabinet, so a sub-panel option wouldn't work.)