My house is 150' long. The main breaker box (pic 1) is at one end of the house and 2 Eaton Pullout Switches at the other end.
The pullout switches power 2 A/C evap coils (pic 3-6). The pullout switches are fed from 40amp breakers at the main (pic 2).
I replaced 1 of the pullout switches with an Eaton BR48L box which has a 220 breaker for the ac and a 220 breaker for a well pump (pic 7).
I have a shed 105' away from these breakers. I wan to run an extension cord down there for some lights and light drill and bandsaw work BEFORE I get my main service put in to feed the shed.
I purchased 250' 10/2 UF-B wire to create a long extension cord.
My plan was to remove the well breaker and put in a 110 20 amp breaker for this new run but there is no neutral bar.
How can I get a 110 outlet, or breaker to wire the 10/2 wire to?