This was working fine, but I had to move the range, and I didn't pay attention when I disconnected it. There is an 8/2 in the wall (black white bare) and the range has 10/3 (red black white bare). I need this back in use. What if I use wall black to range black, wall white to range red, and then wall bare (ground) to range ground and white? After all, don't white and bare go to the same place in the breaker box?