The picture describes it better than I can, but here is the plan. Run a circuit off the panel (hot, neutral, ground) into a GFCI. Off the load side of the GFCI run wires into a light switch box that will control two sets of lights (all lights plugged into outlets). The hot will be pig tailed in the light switch box to feed both switches, while the neutral passes straight through to the first outlet box. In this outlet box I will pig tail the neutral (now have two hots and two neutrals in this box). These two sets of wires will supply two separate sets of lights.
Is this plan valid and safe?