Make/Model of furnace: Bryant / 310AAV042090
Link to Installation Instructions: https://www.carrierenterprise.com/bryant-legacy-80-afue-90-000-btuh-multipoise-gas-furnace-310aav042090#tab-documents
I've reconnected my whole house humidifier but wanted to run by what I did with an expert or someone who's done this before. Don't want to ruin my furnace.
The inspector said it wasn't working and sure enough, it doesn't work. I started troubleshooting the setup and everything looks good until the wiring from the humidifier enters the furnace and ends at some kind of relay. There's no wiring from the furnace to the relay so there's no power or communication from the furnace to the humidifier.
I started looking around the circuit board to see if there were any wires or plugs dangling that needed to be plugged in. That's when I noticed this piece of wiring laying on the floor next to the furnace. It seems to be the connection between the relay and the furnace circuit board.
So, I did some research and looked at some wiring diagrams and it looks like I need to do the following: The end of the wire with the two connectors connects to the relay, doesn't seem to matter what order but I matched the red and the white on the top. Then the end with one connector and one bare wire goes to the circuit board. The connector goes to the HUM and the bare wire goes to the COM 24V. Is this the correct way to wire this?