I have a 14-2 cable at the light switch in my room. White is my hot, black is my switch leg. At my light I have some older cloth braided sheathed wire. This also is a two wire nothing is labeled.
Assuming my cable from my switch splices in a box somewhere and then transitions to this cloth braided wire to my light, how was this light not running with a neutral? Could the neutral be picked up somewhere else maybe on a receptacle? The same two wires (cloth braided) at my light are the same two at my switch cable. I ran continuity and they for sure are the same two. To my understanding there was no neutral, correct? Trying to figure this out and it’s killing me cause i can’t find the box where the wires transition.