Please point out any safety issues with this breaker box in my shop.
has its own service drop and weatherhead
the ground wire is in the center doubletapped and connected to a grounding rod outside
the orange 30amp has no ground connected to the box because the outlet itself is grounded to its own Grounding rod as it is a single circuit for an RV
Criticize away I would like my shop to be safe.. not having any problems presently
Second area of interest.. the power is coming from a splice off the main service AFTER the meter but before the main panel for my house .. all three service cables are done in this manner which should mean that they are not connected at the main box and serve as their own service I believe.
Don't get me started on the main panel it is an ungrounded fuse box, but the main circuits have a similar breaker box and splice and drop due to a previous addition.. I've had no problems with it..
Let's start with the shop.. if I need an electrician I'll hire one I already had one come out and he didn't seem too concerned with the way it was but he is 71 and said they used to do this all the time.