I had to replace an improperly used plastic ceiling box with a metal box to correctly ground existing old armored cable. I thought I took a picture of the box before but I don't have it so I'm having trouble reconnecting the light. Off of this box are:
- Single pole switch for overhead bedroom light
- Two 3 way switches for bedroom closet and hallway light (both go on and off at same time)
With how it is currently wired, the single pole switch/light are working and the closet light is working with the 3 way switches. I am not sure how to reconnect the hallway light so that it also goes on/off with the closet light and 3 way.
Thanks in advance.