I am trying to replace a GFCI and a switch that share the same box, the old one had line and load opposite of the new and and I have now gotten lost.
I have 4 black wires 2 white and 1 ground, hot wire has the green tape and tested no other hot wires and I have paired off the other black and white wires with electrical tape.
I have the live wire connected to the common on the switch, no idea what to connect to what from here! Please help.
The breaker is off.