# Which wire is line vs load wires

Which wire in this configuration is line and subsequently which ones are load?

Legend: B1-B6 are 6 black wires.

Not shown: each switch has ground wiring as well. Left them out for simplicity. There is also a clump or neutral white wires in the back of the box with a wire nut around them all.

Context: Two light switches where the left switch controls lanterns next to a front door and the right switch controls a light post. They are independent. Turning either off doesn't affect the power to the other.

Background: I’m wiring in a smart switch Caseta by Lutron and it has a black line in and red load out. I want to swap the right switch with this and need to know which of the existing two blacks is line in vs load out to the light.

Commentary:

The electrician used a red wire nut, not sure if that was intended to indicate something about all of those black wires.

I was a bit confused by this configuration because my assumption is that B1 is line, and through the left switch it caries power up to the red-capped pigtail and that feeds power to the right switch via B5. However when left switch is off, right switch still works.

My assumption is B1 is line, B3 and B4 go to each of the lanterns, and B6 goes to the pole. B2 and B5 join the switches.

• Is there a problem you are trying to solve ? Commented Feb 22, 2020 at 20:44
• Trying to wire in a smart switch that has a wire for line (black) and red (load) so I’m trying to figure out of the existing blacks, where hot is really coming in vs load that carries the current. Commented Feb 22, 2020 at 22:04
• J Dilly, you should add that pertinent info to your question. Smart switch for which fixture ? And a photo of the box might help. Commented Feb 22, 2020 at 22:23
• Updated question with background, Alaska Man. Commented Feb 22, 2020 at 22:55
• @j dilly Presumably you know what switch you want to replace ?? ( I.E. Which switch controls the fixture you want the new smart switch to control.) Wire it up the same? Do you have a non-contact voltage tester so you can actually test which black wire is bringing in the power ? ( assumptions are not sufficient, nor can we test it from here. ) And a photo of the box might help. Plus: Jack asked about the "neutral, white, wires" Commented Feb 22, 2020 at 23:11

## Those colors

OK, so B2-B5 (blacks I assume?) are hot all the time, and would be even if B1 and B6 were disconnected. Those four wires perform the following 4 jobs (and I really don't care which is which, as it's irrelevant):

• Always-hot from the supply
• Always-hot onward to other points of use
• Always-hot to switch 1
• Always-hot to switch 2

## I like to force particular color codes

Now, cables are made in particular colors, but that does not reflect what functions those wires actually do. I like to re-mark wires using colored tape, using the following color code: :

• Bare, green, yellow-green: Ground (mandatory per international law)
• White or gray - neutrals (mandatory per NEC)
• Black - always-hot (unswitched)
• Red - switched-hot e.g. to a lamp
• Blue - alternate switched-hot
• Yellow - 2nd alternate switched-hot
• 2 yellows together = 3-way travelers
• 2 blues together = alternate 3-way travelers
• 2 reds together = 2nd alternate 3-way travelers

B2-B5 are always-hot and are already black. I would recolor B1 to red... and B6 to blue. And also recolor the wires that they splice to from the wall. So now that your wires are identified, they are same color to same color.

## The colors of wire nuts

Colors of wire nuts are a different deal. They designate wire nut size. Red is "the biggest in ordinary use". Yellow is next down, fit for 2-3 and sometimes 4 #14 wires. Orange is good for 2 wires. They have a lot of overlap in their ranges, but for instance four wires would be too much for an orange.

Their ranges are published and it's best to stay near the middle of the nut's working range. You can stretch a yellow to work where a red is ideal, but better to just use a red.

• Thank you. This is VERY helpful and aligns with the thinking of JACK. I didn’t think of it this way. Also great points about color coded and but colors meaning size. Commented Feb 22, 2020 at 22:53

OK, based on this highly technical drawing I'm going to say that B2, B3, B4 & B5 are all connected and hot. one of the B's is the feed and is connected to a feed out. B2 and B5 make both switches hot. B1 would then control the lanterns and B6 would control the post light.

Now you've stated that the grounds have not been shown. You also seem to be missing some neutral, white, wires that would be connected to all these lights, to the line feed in and the line feed out. How about that?

• Thank you! You are correct that there is also a clump of neutral white wires. I also did not include them because they are all in a wire but in the back and not connected to either switch. Commented Feb 22, 2020 at 22:03

To answer your question further: B2 and B5 are considered "line" and B1 and B6 are considered "load'. Line supplies the power (hot side) to the switch and the load side of the switch (switched hot) is delivering the current to the device being energized. In this case - lights.
In your question you just had the flow going the opposite way.
Edit
Typo correction; B2 and B5 are "line" and B1 and B6 are load.

• @Harper - Reinstate Monica - Thanks! Commented Feb 23, 2020 at 3:40