I had a load bearing wall removed, to make a long story short, I forgot to take pictures of the wiring and now I’m stuck in a jam.
Had a ceiling fan that was fed from a 3way switch but there was only one switch. Power source was coming into the switch box, then 3 way wire was used to feed the ceiling fan and 2 other wall outlets all from the ceiling fan box. Where it gets confusing is that the hot (black) and common (white) fed power directly to the outlets (wall plugs) and the red wire was tied to the white and black wires of the light fixture.
My problem is that I can’t remember the wiring inside the switch box where the power source connects to the switch and the 3 way wire. Any help here would be beyond appreciated. Thanks folks.