I am aware of most NEC codes and am actually asking if this is allowed, There really shouldn't be any reason..I also fully understand keeping my netural and ground seperate and how the bus bars are bridged and grounding case screw etc.
But I could be missing something..And the basic reason for the question..instead of purchasing a larger panel I have a few of these laying around....
I do know you can power the bus bars via a circuit breaker.
Can I also use the actual lugs on that bus bars to send that power to another lug type panel... I do not see why not if connected correctly.
The picture explains pretty clear... I wanna double up the cheapos. They will be connected with 2in+ PVC to which I could never go over my conduit fill. I also am aware there is nothing stopping me from 'butting' them up to one another withe the open holes.