My daughter’s bedroom has 4 outlets. 1 of the outlets is connected to a wall switch. All 4 outlets are currently out and each is an open neutral (ground-hot=120V; neutral-hot=0V). I checked the breaker and it appears to be fine (ground-hot=120V; neutral-hot=120V). The switch is also functioning properly I think (I get the same voltage readings in the on/off positions as I do for a different bedroom with an identical 4 outlet + switch setup).
What could be the issue that’s causing all four outlets to fail and be open neutral, and also how did this even occur given that 1 is on a switch? I’m basically going to replace all four outlets and the switch and hope for the best.
I’d love to hear any ideas you have on how to identify the culprit.