Have three gang hall bath switch panel in which the first two control the fan and light; third does nothing. Have tested all outlets and other lights; third switch seemingly inert yet wired to other two, with lone red wire. Current tester across switch yields no current regardless of switch position.
Just want to lose third useless switch and replace with blank. Anyone got easy solution?