Last fall, I had a cover break to an outdoor outlet. I haven't used it since.
I wanted to replace it today. What I've discovered is that the outlet seems to have no power going go it somehow.
All the lines on the break when turned on, and if I disconnect everything, my tester reveals no power to the line.
I've tested all the outlets on the line, including some INDOOR GFCI outlets in my kitchen, and the rests for them all come up working as normal.