I am having a house built, and I noticed there was no exposed ceiling box at the locations of my pendant lights. I was unable to get out there to visually verify things before drywall went up (that's why there's a construction manager) The CM reassures me everything is wired, inspection passed, and ready to be pulled through on the final set out.
I walked through the attic this morning to find nothing more than a bundle of romex hanging from a roof truss, coming from the light switch location.
I've never seen a new construction rough in without a ceiling box for each light fixture, and this includes other houses this CM is building.
Is this cause for concern? Should I require another electrical inspection for this? The attic will be blown in, concealing anything wrong, for the final inspection.