Below is a picture of the current conduit and wire setup for my new underground service into my house with generator automatic transfer switch and manual transfer switch to allow me to switch to an inlet.
The conduit is all very well secured by the ground and the boxes. The piece of SER wire between the meter pan and transfer switch is only secured at the boxes.
What does code require that I do to secure the conduit and/or SER? I'd like to get that squared away before I call for inspection. I am in NJ and we follow the 2014 NEC.