I currently have a dedicated 15A breaker connected to 2 outlets (with GFCI) in a bathroom using 14/2. These 2 outlets are all that is connected to the breaker.
I plan to add some recessed lighting which would total about 2.2A if all lights are on (20 x 13W). It seems to be a general rule to put bathroom outlets (or outlets in general) on a dedicated circuit. However, it would be very convenient for me if I was able to tap into this circuit to add the lights.
It would be very unusual for all the lights to be on at the same time and even more unusual for them to all be on while using a high draw appliance such as a hairdryer. I would use 14 AWG.
Any thoughts on whether this would present me a problem?