Wiring in ceiling.1I'm trying to replace my kitchen ceiling light fixture but... coming out of the ceiling I have 3 black wires, 3 white wires, a red wire and a ground! I didn't take a picture of how they were wired before removing old fixture - yes, I know. The new fixture only has a black, a white, and a ground.Please help!! Thanks
If your wiring is standard and NEC-compliant:
One cable is the feed, one is te line gouing to next lamp, the third (that has 4 wires: red, black, white and copper) is the wire from the switch.
Just connect whites together (the 4 from wall + one from the fixture), the blacks coming (from wall) together, and the black from the fixture to the red (from the switch)
If you're not sure / don't know how to check, hire an electrician to have it fixed