Standard Trane split heat pump, condenser outside blower inside. Usually the system will run normally but after 2 min 20 seconds the blower motor will cycle on and off randomly for 20 seconds. Then run perfectly for the rest of the heating cycle. One time the problem occurred at 3 min 20 seconds. Expert checked system and said needed new motor. Now has new motor but still same problem. Anybody have any ideas.