Hot wire had burned through due to AC cranked on high. 15 amp Breaker did not trip. I added a jumper to the hot and replaced the receptacle, matching the original installation. When I tried to connect the hot jumper, it caught fire. Old house, wiring 40 years old. I will hire an electrician, but what is wrong?