If I turn my fan on on my thermostats the heat pump turns on with heat or cool setting
There is a jumper wired from green to w1(the heat pump)
If I move the jumper to r (24v) and g and turn on the dip swith 8 (on - fan comes on with call for heat off - fan comes on with cool call) will it fix my problem?
I’m assuming I would have to adjust the dip switch for summer or winter?
We recently got a wood stove in step down den and it has a blower so we want to run the fan to circulate the heat from it